OneVue Network Profile the device will connect to. For a Non-DHCP network, you are required to provide the device's static IP address.
From the OWDC app, you cannot create a new network or edit its settings. Before you begin, from OneVue verify the network exists or add a new network.
What is the sensor monitoring?
Its assigned Monitored Asset. If assigning to an existing Monitored asset, enter the exact name as it appears in OneVue, or option to create a new Monitored Asset.
OneVue Business Unit assigned to the sensor and its assigned Monitored Asset. From the app, you cannot create a new Business Unit.
Normal Condition (Range)
The Normal Condition (range) is the expected, normal operating condition of the Monitored Asset and is dependent on sensor type.
Temperature: low to high range in Fahrenheit or Celsius.
Humidity: low to high range in RH.
Differential Pressure: Positive or Negative pressure and either the Minimum or Maximum INH20 or PASCAL.
Water Leak: Normal Condition is always set to Dry and cannot be changed.
Contact Closure: Normal Condition is always set to Closed and cannot be changed.
From your Android device, open the OWDC app.
Enter your OneVue username and password (required to be assigned to the Account Admin Role).
Remove AC power from the sensor device. During the next step, it receives power from its connection to your Android device. If battery power is enabled, leave this on.
Set the Sensor into configuration mode > connect the sensor to your Android device using a USB OTG or a USB C cable (dependent on your device).
App displays "Add Device" and "Con" displayed on Bridge LCD screen, indicating it's in configuration mode.
To assign or update its network > select a Network Type > select an available network > select Next.
Configure or edit its primary settings. For a dual type sensor, this step appears twice.
What are you monitoring?: either enter a new Monitored Asset or if assigning an existing OneVue Monitored Asset enter its exact name.
Business Unit: select an existing Business Unit. If you edit the current assigned Business Unit, the Business Unit assigned to the sensor and Monitored Asset are both updated.
Normal Condition (Range): enter expected normal condition for what the sensor is monitoring (Monitored Asset).
The app configures the sensor and displays its configuration status.
Do not remove the connection between the sensor and your Android device until prompted.
When the Disconnect Device message appears, remove the USB connection between the sensor and your Android device and re-apply AC power to the sensor.
Once disconnected, the app verifies the device successfully checked-in to OneVue. If after 15 minutes it does not check-in, the app displays a status message.
Temp Sensor only: may display an Err message due to no probe connection. Insert probe into sensor jack and press and release the sensor Alarm Silence button to clear the error state and reset the Lo/Hi Collection Period.
All sensor models: If applicable, it may also take time to download the latest firmware (sensor LCD displays UP).
You can now configure additional sensors or close the app when you’re done.