This form is required to be completed and provided to Primex prior to installation. Failure to meet these requirements or not providing complete and accurate information may affect system coverage - resulting in installation delays and additional charges. System setup examples are provided for reference.
The information below specifies the pre-installation requirements for a Primex72MHz Wireless Clock System. Prior to system installation, Primex is to receive acknowledgment that all requirements have been met.
Failure to meet these requirements or not providing complete and accurate information may affect system coverage - resulting in installation delays and additional charge
The following photos are required to be provided to Primex.
Outdoor roof area that identifies external antenna planned install/mounting location.
Other existing antennas on roof.
Outdoor antenna grounding location.
Outdoor existing penetrations that can be used for XR system cables.
Indoor location of the Transmitter’s grounding location.
Building penetration for cable routing may be required.
Client is responsible to verify local codes for conduit requirements and provide details to Primex prior to install date.
If conduit is required, Client must provide and have installed prior to Primex system installation. A minimum of 1.5 inch (4 cm) conduit size for GPS cabling only. A minimum of 1.75 inch (4.5 cm) conduit size for antenna cabling only.
If cables are run together, a minimum of 2 inch i.d. of conduit (5 cm) is required. A review of conduit installation is REQUIRED to be completed, prior to site visit, with Primex if running both cables together.
If plenum rated cables are required, Client is to notify Primex. Plenum cable is an additional charge if not previously purchased.
Ethernet network port must be located within 5 ft. (1.5 m) from the Transmitter.
Network Port 123 is open to allow connection to system time source.
By default, Transmitter is factory configured to obtain a time from the National Institute of Standards and Technology (NIST). If a time source other than NIST is required, Client is to provide the IP address for the designated NTP Server.
NTP Server Address (if applicable).
Site preparation is the responsibility of the Client prior to installation of the system. If these requirements are unable to be fulfilled or installation needs differ at the time of installation, additional installation materials and procedures may occur. Additional expenses incurred are the responsibility of the Client.
Prior to the on-site arrival of a Primex technician, all system equipment and components must be delivered to the room where the Transmitter installation is going to occur.
Site specific requirements for Transmitter shelf mounting or enforcements are the responsibility of the Client.
Transmitter with External Antenna site requirements.
Building roof access is required. If local permits are required to access roof, these must be obtained by Client and approved by Primex prior to installation.
For non-penetrating masts, Client is responsible to supply cinder blocks. Client must verify any non-penetrating mast local codes or levels are met (hurricane level 3 requires six cinder blocks, hurricane level 4 requires eight cinder blocks, hurricane level 5 requires nine cinder blocks).
Client is to provide access to ladder that meets requirements of site installation.
To be compliant with OET65, Client is responsible to place and maintain an antenna sign either on an exterior door or roof hatch leading to the antenna.
Adding additional cabling may impact the performance of the signal. Primex is not responsible to provide additional product to fill coverage gaps.
For illustration purposes only. Drawings not to scale. For complete instructions, refer to installation guide.