The following step begins by selecting the Monitored Asset assigned to the sensor, which is the recommended method. This ensure the correct sensor monitoring the asset is selected.
Go to Monitoring > Monitored Assets.
From the list, select the Monitored Asset link. Its profile is displayed.
From the sensor type section, select the type of sensor (its assigned sensor). The sensor profile is displayed.
Set its Normal Condition. The setting varies by the sensor type.
Temperature: low to high range in Fahrenheit or Celsius.
Humidity: low to high range in RH.
Differential Pressure: Positive or Negative pressure and either the Minimum or Maximum INH20 or PASCAL.
Water Leak: Normal Condition is always set to Dry and cannot be changed.
Contact Closure: Normal Condition is always set to Closed and cannot be changed.
When a setting update is made to a device, its Update Pending status is set to Yes. During its next check-in, all pending setting updates are downloaded to the device. Once downloaded, its Update Pending status is set to No.