A bridge is required to be set to No Network Mode when the facility's network is not available during installation. During this mode, the bridge does not connect to the facility's network to check-in to OneVue or obtain UTC time from a NTP Server. During No Network Mode, the bridge is configured with local time with use of the Primex Device Configuration software. This allows the Sync Bluetooth clocks and repeaters to receive local time during their connection to the mesh network.
When the facility's network is available, the device must be set back to Normal (Bton) mode to allow its network connection to the facility's network.
Bridge requires AC power when operating in No Network mode. When operating on battery backup-power, estimated battery life is only up to one day.
From the bridge front display, press and hold the silence button for 3 seconds.
Verify NoNt is shown on its LCD display. This indicates it's in No Network mode.
Next, configure the bridge with your computer's local time.
The bridge sets its internal time to your computer's local time. If you want to bridge to receive time from a different time zone, change your computer's time zone before beginning this procedure.
Do not remove power from the bridge during this procedure - it must remain powered on at all times.
Download and install the Primex Device Configuration software.
Installation requires administrator permission and a computer with Windows® 7 or 10 (32 and 64-bit). If you do not have administrator permission, contact your IT department to install the software.
Plug the supplied Primex USB configuration cable into a USB port on your computer.
Plug the configuration cable mini-USB connector into the bridge's USB mini port.
The bridge detects the connection to your computer and enters configuration mode. The LCD displays the letters Con and the Config icon is displayed indicating the device is in configuration mode.
Open the Primex Device Configuration software. Go to All Programs > Primex > Primex Device Configuration or from your computer desktop, double-click on the Primex Device Configuration icon.
From the Enter Password window, enter the factory default password (case sensitive) - Primex1
Select Connect. A connection between your computer and the bridge is established.
Verify the notification area located in the lower-left of the screen, displays Connected to clock bridge device on COMx, which indicates the connection is established.
Select Read Configuration.
Select Write Configuration. From the Confirmation Needed window, select Yes
Select Disconnect. The connection between the software and device is ended.
Remove the USB connection between the bridge and your computer.
You can now begin installing Sync Bluetooth Clocks and Repeaters.
When a network is available, the bridge must be set to normal mode to allow its connection to the facility's network.
From its front display, press and hold the silence button for 3 seconds. This forces the bridge to exit No Network mode.
From its LCD screen, verify Bton is displayed. Which indicates it's no longer in no network mode.
Power cycle the bridge. It then enters deployment mode.
Press and release the check-in button to initiate a manual check-in. This validates the bridge can connect to the facility’s network and OneVue.
Its LCD screen displays a series numbers indicating its check-in connection sequence.
Verify its LCD screen displays Signal OK and Bton (normal mode). Signal Ok indicates the bridge connected to the facility's network.