The Differential Pressure Sensor door monitoring feature is designed to allow the status of a magnetic door switch and the sensor's Door Delay setting time period to manage when a monitored asset is set to the Alarms Disabled state. When set to the Alarms Disabled state, OneVue does not monitor the differential pressure readings or the sensor device operating status and will not generate alerts for the Monitored Asset.
Go to Monitoring > Monitored Assets.
From the Monitored Asset column, select the link of the Monitored Asset. The Monitored Asset profile is displayed.
From the sensor section, select the Differential Pressure link. The sensor profile is displayed.
Select Show Advanced Options.
From the Door Delay, set the number of minutes.
When the door switch has remained in an Open status for longer than the sensor's Door Delay setting, the sensor and its assigned Monitored Asset (room) is automatically set to an Alarms Disabled state with a status of Past Door Delay.
During the Alarms Disabled state, the sensor device continues to transmit its readings and operating statuses, but the data is only logged and stored in your OneVue account. OneVue does not monitor the sensor readings or device operating status and disables the alerts assigned to the Monitored Asset during the Alarms Disabled state.