This topic provides the steps to configure InfoBoards that are not part of a OneVue Notify Monitor subscription. InfoBoards configured for standalone use are not monitored by or managed from OneVue.
Each OneVue Sync Transmitter is configured, installed, and operating.
If the InfoBoards will use NTP as its time source, up to three NTP IP addresses can be configured.
Apply power to InfoBoard.
From your mobile device, open the OneVue Device Configurator (ODC) app .
Set InfoBoard into Bluetooth discoverable mode: press and release its Bluetooth pairing button.
Button is located in its backside connection panel. It's best to use a paper clip or similar object to press and release the button.
Select Standalone use.
From available devices, select the InfoBoard 12-character MAC address (printed on a label affixed to its back panel).
IB403: Indicates Large InfoBoard model
IB402: indicates Medium InfoBoard model
IB401: indicates MiniBoard model
If the InfoBoard is not listed, select the app Refresh icon.
Confirm its Network settings and select Continue.
By default, set to use a DHCP network. If using a Non-DHCP network, turn DHCP Off and enter the static IP network settings.
Configure its primary settings.
Name: unique name of the device. Commonly set to identify its install location.
Time Zone: select the install location Time Zone.
Configure its display settings, select Advanced.
Display Mode Settings: 12- hour mode (default) or 24-hour mode.
Color Settings: set the character color for Time, Date, and Timer. Options are limited to Red (default), Green, and White.
Time Source: set to receive time updates from Transmitter (default) or from a NTP server by selecting Manual NTP Configuration (requires Ethernet connection). If set to NTP, enter three NTP server IP addresses.
Firmware: update firmware version only when directed by Primex Technical Support.
Select Save to complete configuration.